Earthing up to 2 MVA 33 kV - Earthing transformers are used to create a neutral point in a three-phase system, which provides possibility for neutral earthing. The earthing can be through an arc-suppression reactor, a neutral earthing reactor or resistor are directly in these earth transformers. Earthing transformers are usually oil immersed and may be installed outdoor. In cases where a separate reactor is connected between the earth transformer neutral and earth, the reactor and the transformer can be incorporated in the same tank.
Neutral earthing transformers are normally provided in 3-phase system, which is without neutral and earth fault protection.
Neutral earthing transformer is having zig-zag (interstar) winding to achieve the required zero phase impedance. In addition an auxiliary winding can also be provided to meet the requirement of auxiliary power supply in these electrical earthing transformers.
ONAN /ONAF cooling with conventional pressed steel radiators. The range includes up to 33 KV systems and as per the site requirements.